# Inspection Of Voltage Drop In Conductors

## Voltage Drop Requirements

It is part of the inspection process to ensure that installed conductors have been correctly selected for current carrying capacity and voltage drop. To check the suitability of the current carrying capacity it is simply a matter of looking at the installation method, and then checking on the current carrying capacity tables for the cable in Appendix 4 of BS 7671.

To ensure that the cable meets the voltage drop requirements is slightly more complex.

A simple method is to measure the voltage at the origin of the circuit, and then measure the voltage at the end of the circuit with the load connected and switched on. The difference between the two measurements will be the volt drop.

If the first method is impractical, then a resistance test should be carried out between the phase and neutral of the circuit. This test is carried out using the same method as the R1 + R2 test although, instead of the test being between phase and circuit protective conductor (CPC), it is between the phase and neutral for the circuit.

Once the resistance R1 + Rn of the circuit has been measured it should be multiplied by the current that will flow in the circuit.

This will give you the volt drop for the circuit.

## Example of voltage drop calculation

A circuit is wired in 2.5 mm2 and is 25 metres in length. The current in the circuit is 18 amps.

The measured value of resistance is 0.37 Ω.

Voltage drop V = I x R

Voltage drop V = 18 x 0.37 = 6.66 volts

This is the voltage drop for the circuit.

Voltage drop in conductor can be calculated by following software and MS Excel Spreadsheets:

Resource: Practical guide to inspection, testing and certification of electrical installations by Christopher Kitcher

Edvard Csanyi

Edvard - Electrical engineer, programmer and founder of EEP. Highly specialized for design of LV high power busbar trunking (<6300A) in power substations, buildings and industry fascilities. Designing of LV/MV switchgears. Professional in AutoCAD programming and web-design. Present on

﻿

1. […] installation conditions and the load it will carryContinuous current rating of the cableVoltage drop and short circuit considerationsEarth fault loop impedanceHere, I am going to describe that how the […]

2. […] In accordance with IEC 61947-4-1 and IEC 61947-5-1, the normal control voltage range of power and control contactors lies between 85 … 110 % of the rated control voltage. Within these limits contactors pull-in […]

3. […] […]

4. […] aluminum is lighter and generally less expensive than copper, a larger cross section of aluminum conductor must be used to carry a current with similar performance as copper. Copper has higher mechanical […]

5. […] systems is that they carry more power for a given current.Higher Voltage DistributionAdvantagesVoltage drop – A higher-voltage circuit has less voltage drop for a given power flow. Capacity – A […]

6. […] first part – Sizing and Protection of the Neutral Conductor (1) Protection of the neutral conductorProtection against overloadIf the neutral conductor is correctly sized (including harmonics), no […]

7. […] for proper identification per the drawings and specifications.2. Equipment and Installation Inspection Items […]

8. […] installed sags and tensions and on proper handling during installation.The final sag shape of conductors is used to select support point heights and span lengths so that the minimum clearances will be […]

CONNECT //
?>